SMART GRID: EEFECTIVE REACTIVE POWER CONTROLLER
- Jul 8, 2021 9:30 pm GMT
Utilities today devote considerable attention to managing voltage levels and reactive power
(VAR) throughout the power transmission and distribution systems. Loads that contain
capacitors and inductors such as electric motors, pool pumps, and the power supplies in
modern electronics put additional strain on the grid, as the reactive portion of these loads
causes them to draw more current than an otherwise comparable resistive load (such as a
light bulb) would draw for the same amount of kilowatts transferred. This extra current
causes the transformer to heat up, which wastes energy and reduces service lifetime.
Uncorrected reactive power makes it harder to stabilize grid voltage. It also drives additional
cost throughout the entire grid since everything wires, transformers, and generators must
be sized to carry the total current.
The more reactive power flowing on a line, the less “room” there is for real power and the
less efficient the transmission and/or distribution system will be.
Improving the efficiency of power transmission and distribution comes down to two
choices: you can reduce the resistance of the wires by making them larger or using better
materials (not a practical solution), or you can improve the effectiveness of the flow of
electricity. To address the latter, it’s important to understand one technical concept and
that is the difference between active and reactive power.
In the last 20 years, this problem has attracted interest from both academia and
industry and this has produced many special devices and algorithms. This article first
introduces reactive power sources and secondly the role of the smart grid to control and
improve the efficiency of power flows.
REACTIVE POWER SOURCES
The controllable reactive power sources include generators, shunt reactors, shunt
capacitors and On Load Tap Changers of transformers (OLTC).
To optimize the movement of electric energy along the power lines, we would ideally like to
eliminate reactive power flows, or at least minimize them. Utilities do this on their local
distribution systems using devices such as capacitor banks or special transformers, typically
located at substations or on feeders. These devices work to keep reactive power flows
down, making the full capacity of the conductor available for real power. Generators: can generate or absorb reactive power depending on the excitation. When
over-excited they supply the reactive power, and when under-excited they absorb reactive
power. The automatic voltage regulators of generators can continually adjust the excitation.
Reactors, shunt capacitors, and OLTC: are traditionally switched on/off through circuit
breakers on command from the operator. Since the early eighties, advances in Flexible AC
Transmission Systems (FACTS) controllers in power systems have led to their application to
improve voltage profiles of power networks. The most frequently used devices are: Reactive
Power Controller (RPC) and Static Var Compensator (SVC).
The RPC connects or disconnects capacitor stages automatically by detecting the phase
divergence between the fundamentals of current and voltage. The measured divergence is
compared with several segmental set phase divergence regions, capacitor contractors will be
switched on or off according to it.
Compared with RPC, the SVC is more advanced electronics equipment. It can provide
continuous capacitive and inductive reactive supply to the power system. The SVC typically
consists of a Thyristor Controlled Reactor (TCR), a Thyristor Switched Capacitor (TSC), and AC
Filters (ACF). From the viewpoint of power system operation, an SVC is equivalent to a
controllable reactor and a fixed capacitor. Its output can vary depending on the level of
generation and absorption of reactive power so as to maintain its terminal voltage at a
In both the techniques described above, the volt/VAr control devices have operated
autonomously, independent of one another, and without centralized coordination. This
approach worked, but it left a good deal of efficiency on the table since actions were taken by one
device might have less-than-optimal results for another location on the grid or for the
system as a whole. Hence the modern and intelligent approach to Volt/Var control is needed to
optimize the grid performance, reduce losses and enhance consumer satisfaction. This can
be achieved through Volt/Var automation.
Advances in automation and communications have laid the foundation to make centralized,
coordinated volt/VAr control possible and the emergence of Volt/VAr automation using
today’s faster computers leads to volt/VAr optimization. This is one of the functions of intelligent/smart grid.
As it is known, is an advanced application that runs periodically or in response to operator
demand at the utility control center or in substation automation systems. Combined with
two-way communication infrastructure and remote control capability for capacitor banks
and voltage regulating transformers. The capacitor banks are equipped with sensors that
automatically trigger the need for reactive power compensation in case of any loss, by
sending signals to the grid or substation automation system. The real-time information
makes it possible to optimize the energy delivery efficiency on distribution systems.
The Role of Smart Grid
The “smart grid” is based on the usage of smart energy technologies—the application of
power control by means of digital information systems (smart meters and smart appliances)
that communicate through the advanced communication technology (i.e. internet) with the
electricity utility—to optimize electrical power system generation, delivery, and end-use
Smart Grid will integrate all the components of the power system to enhance the performance
of the grid. Much of the integration of components relates to communication systems, IT
systems, and business processes. And to achieve this, a Smart grid, real-time data, and active
grid management require fast and two-way digital communication.
Electric utilities use a wide variety of telecommunications including:
• Wired and wireless telephone
• Voice and data dispatch radio
• Fiber optics
• Power line carrier
• The internet
_ Hybrid fiber cable (HFC)
_ Digital subscriber line (DSL)
_ Broadband over power lines (BPL)
_ Wireless (wi-fi and wi-max), and
_ SatelliteThe real breakthrough here is in the communication speed and quality of the computation
since the smart grid network uses advanced algorithms to identify the optimal operation
strategy from millions, or even billions of possibilities, arriving at a result fast enough to
apply it in real-time utility networks.
Smart grid plays a vital role in the utilities quest to deal with reactive power control in a
smarter, faster, and efficient manner. This result improved grid efficiency reduces the
amount of power that must be generated, hence dealt with the reactive power effect on
the grid, it also improves power factor and can result in substantial savings in the cost of energy
and infrastructure utilization and with it the emissions of CO2 and other pollutants
associated with power generation can be minimized significantly.
Get Published - Build a Following
The Energy Central Power Industry Network is based on one core idea - power industry professionals helping each other and advancing the industry by sharing and learning from each other.
If you have an experience or insight to share or have learned something from a conference or seminar, your peers and colleagues on Energy Central want to hear about it. It's also easy to share a link to an article you've liked or an industry resource that you think would be helpful.